# Power distribution units for Universal V2B Rack

The Universal V2B Rack is equipped with specific power distribution units (PDU) for Americas, APAC, and EMEA regions. The PDUs can provide electrical power to the racked system in a single-phase or three-phase configuration.

- Before installing third-party devices into the rack, check the electrical current draw of each device. Verify the electrical specifications and allowable current load on each PDU before plugging the device into the PDU.
- Balance the electrical current load between available PDUs.

## Americas single-phase PDU 1P30A-8C13-3C19UL.P

The following figure and table describe the specifications of the PDU.

Part Number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

1P30A-8C13-3C19UL.P |
Americas |
6/rack 3/side |
Single phase 208V, 30A (24A rated) 60Hz Delta/wYe: N/A NEMA L6-30P input power plug 4.5 m (14.76 feet) cable |
8 IEC C13 + 3 IEC C19 sockets Max allowable current: 24A 5kVA | 72A (15kVA) |

## Americas single-phase PDU 1P30A-15C13-3C19UL.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

1P30A-15C13-3C19UL.P |
Americas |
4/rack 2/side |
Single phase 208V, 30A (24A rated) 60Hz Delta/wYe: N/A NEMA L6-30P input power plug 4.5 m (14.76 feet) cable |
15 IEC C13 + 3 IEC C19 sockets Max allowable current: 24A 5kVA | 48A (10kVA) |

## Americas three-phase PDU 3P30A-8C13-3C19UL.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P30A-8C13-3C19UL.P |
Americas |
6/rack 3/side |
Three phase 208V 3P, 30A (24A rated) 60Hz Delta/wYe: Delta NEMA L15-30P input power plug 4.5 m (14.76 feet) cable |
8 IEC C13 + 3 IEC C19 sockets Max allowable current: 38.4A 8kVA | 115A (24kVA) |

## Americas three-phase PDU 3P30A-15C13-3C19UL.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P30A-15C13-3C19UL.P |
Americas |
4/rack 2/side |
Three phase 208V 3P, 30A (24A rated) 60Hz Delta/wYe: Delta NEMA L15-30P input power plug 4.5 m (14.76 feet) cable |
15 IEC C13 + 3 IEC C19 sockets Max allowable current: 38.4A 8kVA | 77A (16kVA) |

## Americas three-phase PDU 3P30A-24C13-6C19UL.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P30A-24C13-6C19UL.P |
Americas |
2/rack 1/side |
Three phase 208V 3P, 30A (24A rated) 60Hz Delta/wYe: Delta NEMA L15-30P input power plug 4.5 m (14.76 feet) cable |
24 IEC C13 + 6 IEC C19 sockets Max allowable current: 38.4A 8kVA | 38.4A (8kVA) |

## APAC and EMEA single-phase PDU 1P32A-9C13-3C19CE.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

1P32A-9C13-3C19CE.P |
APAC and EMEA |
6/rack 3/side |
Single phase 230V max. 32A (25.6A rated) 50Hz / 60Hz Delta/wYe: N/A IEC309 P + N + E input power plug 4.5 m (14.76 feet) cable |
9 IEC C13 + 3 IEC C19 sockets Max allowable current: 25.6A 5.9kVA | 77A (17.6kVA) |

## APAC and EMEA single-phase PDU 1P32A-18C13-3C19CE.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

1P32A-18C13-3C19CE.P |
APAC and EMEA |
4/rack 2/side |
Single phase 230V max. 32A (25.6A rated) 50Hz / 60Hz Delta/wYe: N/A IEC309 P + N + E input power plug 4.5 m (14.76 feet) cable |
18 IEC C13 + 3 IEC C19 sockets Max allowable current: 38.4A 8.8kVA | 77A (17.6kVA) |

## APAC and EMEA three-phase PDU 3P16A-9C13-3C19CE.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P16A-9C13-3C19CE.P |
APAC and EMEA |
6/rack 3/side |
Three phase 400V max. 16A (12.8A rated) 50Hz / 60Hz Delta/wYe: wYe IEC309 3P + N + E input power plug 4.5 m (14.76 feet) cable |
9 IEC C13 + 3 IEC C19 sockets Max allowable current: 38.4A 8.8kVA | 115A (26.4kVA) |

## APAC and EMEA three-phase PDU 3P16A-15C13-3C19CE.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P16A-15C13-3C19CE.P |
APAC and EMEA |
4/rack 2/side |
Three phase 400V max. 16A (12.8A rated) 50Hz / 60Hz Delta/wYe: wYe IEC309 3P + N + E input power plug 4.5 m (14.76 feet) cable |
15 IEC C13 + 3 IEC C19 sockets Max allowable current: 38.4A 8.8kVA | 77A (17.6kVA) |

## APAC and EMEA three-phase PDU 3P32A-24C13-6C19CE.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P32A-24C13-6C19CE.P |
APAC and EMEA |
2/rack 1/side |
Three phase 400V max. 32A (25.6A rated) 50Hz / 60Hz Delta/wYe: wYe IEC309 3P + N + E input power plug 4.5 m (14.76 feet) cable |
24 IEC C13 + 6 IEC C19 sockets Max allowable current: 77A 17.6kVA | 77A (17.6kVA) |

## Americas, APAC, and EMEA three-phase PDU 3P30A-243-69CE-UL.P

The following figure and table describe the specifications of the PDU.

Part number |
Region |
Quantity |
Power input per PDU |
Power output per PDU |
Total rack amperage available |

3P30A-243-69CE-UL.P |
Americas, APAC, and EMEA |
2/rack 1/side |
Three phase 400/415V max. 30/32A (24A rated) 50Hz / 60Hz Delta/wYe: wYe IEC309 3P + N + E input power plug 4.5 m (14.76 feet) cable |
24 IEC C13 + 6 IEC C19 sockets Max allowable current: 77A 17.6kVA | 77A (17.6kVA) |